Get useful tips, reminders, product notices, and discount offers.
We respect your email privacy
Email has been sent to you , please check your spam/junk emails if you are unable to find the email.
Due to some internal error, the mail has not been sent.
Provides protection from two hazards – fire and CO – in one unit with Intelligent sensor.
Smoke alarms are powered by battery or by your home's electrical system. If the smoke alarm is powered by battery, it runs on either a disposable 9-volt battery or a non-replaceable 10-year sealed lithium battery. Alarms that receive their power from your home's electrical system (hardwired alarms) usually have a back-up battery that will need to be replaced once or twice a year.
There are two types of sensing technology available. Ionization sensing alarms may detect invisible fire particles (associated with flaming fires) sooner than photoelectric alarms. Photoelectric sensing alarms may detect visible particles (associated with smoldering fires) sooner than ionization alarms. Kidde strongly recommends that both ionization and photoelectric smoke alarms be installed to help insure maximum detection of the various types of fire that can occur within the home.
There are many special features that can help protect you and your home, or make your safety products easier to maintain and operate. Many of these features are not well known by their name, so to learn more about specific features of a model, select it and view its detail page.
The Kidde KN-COSM-XTR-BA uses breakthrough technology to offer a fast response to real fires, including smoldering and fast-flaming, as well as protect you from carbon monoxide and dramatically reduce the chance of nuisance alarms. In addition, the Intelligent Alarm contains a voice warning that clearly states the present danger – smoke or carbon monoxide – and announces “FIRE!” or “WARNING! CARBON MONOXIDE!” The Intelligent Alarm combines the detection capabilities of an ionization smoke sensor – which is more likely to detect smaller, less visible fire particles, like those produced by flaming fires – with that of an electrochemical sensor, which is used to detect CO.
Since carbon monoxide is present in all fires, having both detection chambers work together in one alarm is a breakthrough in the fire safety industry. When either sensor notices a potential hazard, it will communicate with the other. Depending on what is detected, the alarm will adjust its smoke sensitivity in order to better discriminate between a real hazard and a false one. This constant communication enhances the alarm’s overall performance in all fires, and significantly reduces the potential for a nuisance alarm.
This alarm uses ionization sensing technology. Leading authorities recommend that both ionization and photoelectric smoke alarms be installed to help insure maximum detection of the various types of fires that can occur within the home. Ionization sensing alarms may detect invisible fire particles (associated with fast flaming fires) sooner than photoelectric alarms. Photoelectric sensing alarms may detect visible fire particles (associated with slow smoldering fires) sooner than ionization alarms.
The red LED will flash and be accompanied by three long alarm beeps followed by a verbal warning message “FIRE!”. The alarm pattern will repeat until smoke is eliminated.
Four short alarm beeps followed by a verbal warning “WARNING! CARBON MONOXIDE!” This continues until the unit is reset or the CO is eliminated.
If any form of battery failure is detected the red LED light will flash and the unit will “chirp” once every 60 seconds for at least 7 days. The “LOW BATTERY” voice occurs once every 15 minutes.The green LED will also be flashing twice per second.
“HUSH MODE ACTIVATED” and “HUSH MODE CANCELLED” voice announcement.
If the alarm had detected a CO level of 100ppm or higher, the unit will announce “CARBON MONOXIDE PREVIOUSLY DETECTED” to warn of the CO incident, when the Test/Reset button is pressed.
Part Number (Ordering Number): 900-0216
The combination smoke and carbon monoxide alarm shall be Kidde Model Number KN-COSMXTR-BA (part number 900-0216A) or approved equal. It shall be powered by 2 AA batteries. The unit shall incorporate an ionization smoke sensor with nominal sensitivity of 0.97 %/ft. The CO sensor shall be of a fuel cell design and shall meet the sensitivity requirements of Underwriter’s Laboratory’s UL 2034 single and multiple station carbon monoxide alarms. The temperature operating range shall be between 40°F and 100°F (4°C and 38°C) and the humidity operating range shall be 10% - 95% relative humidity, non-condensing. The combination alarm can be installed on the surface of any wall or ceiling following the UL/NFPA/Manufacturer’s recommended placement guidelines. The alarm shall provide optional tamper resistance that deters removal of the unit from the wall or ceiling. The alarm shall include a test button that will electronically simulate the presence of smoke and CO and cause the unit to go into both modes of alarm. This sequence tests the unit’s electronics to ensure proper operation. The CO sensor will not alarm to levels of CO below 30 ppm and will alarm in the following time range when exposed to the corresponding levels of CO. 70 ppm CO Concentration 60 – 240 minutes 150 ppm CO Concentration 10 – 50 minutes 400 ppm CO Concentration 4 – 15 minutes The combination alarm shall have two methods of warning for danger: a piezoelectric horn that is rated at 85 decibels at 10 feet and a voice warning that identifies the danger. For a CO incident, the horn will sound in the repetitive manner -- four (4) fast beeps, a short pause, four (4) fast beeps, a short pause. In between, the unit will announce “WARNING CARBON MONOXIDE!”. In a Smoke incident, the horn will sound in the repetitive manner -- three (3) beeps, a pause, three (3) beeps, a pause. In between, the unit will announce “FIRE!”. The unit shall also indicate a low battery warning utilizing each of the following methods: a brief alarm chirp, the voice announcement of “Low Battery!” and the red LED will flash once per minute. The unit shall incorporate 2 LED’s. A green LED will flash every 60 seconds in standby condition. A red LED will flash during smoke or CO alarm, and in error mode. The unit shall at a minimum meet the requirements of UL 2034, UL217, NFPA72, (chapter 11 2002 edition) The State of California Fire Marshall, NFPA101 (One and two family dwellings) Federal Housing Authority (FHA), Housing and Urban Development (HUD). It shall also include a 10-year manufacturer’s limited warranty.